This project arises from the need for a medical clinic that produces air, medical air unlike the common air is that this is dried and filtered great, for this high filtration systems are used. after performing several processes finally air is delivered to patients by an internal network of copper pipes. To ensure that the air is very pure, it was analyzed in two variables, one of which is carbon monoxide indicating the purity of the air and the other is the dew point representing humidity, carbon monoxide not may exceed 10 ppm and the dew point can not exceed 4 ° C. for this two monitors they are showing the value of these two critical variables implement. Since the production of medical air never stops (24/7) need to know what the traceability of variables to ensure that the product is suitable, right there is where the solution is deployed LinkIt UNO, the development of telemetry system is constantly analyzing the behavior of these variables, graphics and the user can view a history of the values of the variables. The system can also send alarms msn and email if any of the variables overflow the required values. As it is a drug for the execution of a qualification was required, this process is to test equipment (challenge to the system) and verify comportment is in critical condition. This fee to perform a specialized medical air production company. The results of the rating were large, the team worked very well and is now up and running for the purpose it was designed.